|« Help With 4 Way Switch Wiring||Electrical Wiring for a Switch Outlet Combination »|
200 Amp Electrical Service Upgrade Riser
©Copyright Dave Rongey -
Dave on Google+
How an Electrical Service Entrance Pipe is Typically Used for a Panel Upgrade – The rigid conduit should be solid from the weather head down to the electric meter enclosure or main service panel.
Service Entrance Pipe for a Panel Upgrade
- The pipe coming through the roof is 2 in threaded and I would be would using a 2 in rigid coupling a 2 in watertight connector into that then EMT into another 2 in water tight connector to the meter socket hub, or do I have to buy a $40 stick of rigid conduit and a rigid connector or have it threaded to be code.
Background: Peter, a Handyman from Milwaukee WI
Thanks for your home electrical wiring question peter.
How an Electrical Service Entrance Pipe is Typically Used for a Panel Upgrade
Skill Level: Advanced – Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific service upgrade.
Estimated Time: Depends on the type of panel and available access to the project area.
Precaution: This is an extensive project that should be performed by a Licensed Electrical Contractor.
Notice: Making changes to the Electrical Service Panel should be done with a permit and be inspected.
- Peter, you can check with your locals electrical codes, however the rigid conduit should be solid from the weather head down to the electric meter enclosure or main service panel.
- If a coupling is needed the it should be placed closest to the electric meter equipment which will allow for a solid length or rigid pipe to penetrate the roof for the service mast.
- Yes, rigid conduit is expensive however it offers the best protection.
- Some areas may allow IMC which is less expensive but it is still a solid conduit.
The Following resources will assist you with your electrical service upgrade:
Home Electric Panel
- House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Electrical Code for Conduit Fill
- Electrical Code
- Electrical Codes for Services
Wiring Electrical Codes
- Electrical Code Articles
- Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, smoke-detectors.
|« Help With 4 Way Switch Wiring||Circuit Loads and Dim Lights »|
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.