|« How to Repair a Kitchen GFCI Circuit||Electrical Wiring for Two GFCI Outlets »|
GFCI Circuit Breaker and Wiring
By Dave Rongey - Summary:|
How to Wire a GFCI Circuit Breaker: Does it matter where in the breaker box panel I insert a 20 amp GFCI 220Volt breaker?
GFCI Circuit Protection Requires Correct Circuit Wiring
- I moved some breakers around and put the GFCI breaker above, closer to the main breaker, a single pole breaker that feeds some outlets.
- Now whenever I plug in a tool with a motor in it and turn it on the GFCI breaker trips and irrigation pump shuts down.
- Do the GFCI breakers need to be last in line in the panel, furthest away from the main breaker ?
- Or should I use a regular breaker in the panel and move the GFCI breaker to the end of the feeder line next to the pump. Or should I be doing or not doing something else.
Thanks for your help,
Background: Rick, a Contractor from Rocheport, Missouri.
Thanks for your electrical wiring question Rick.
How to Wire a GFCI Circuit
- The location of the GFCI circuit breaker does not affect the operation.
- I’m curious – what are you providing power for that requires a GFCI Circuit breaker, and – if this device actually requires GFCI protection, have you installed all the necessary wiring?
- For example, most spas and hot tubs require a 4-wire GFCI circuit where a separate neutral wire is required.
- If you are providing 240 volt power to an agricultural pump that does not require GFCI protection or a separate neutral then you just need to install a regular 2-pole 240 volt circuit breaker.
- Make sure to install the wiring as required for the specific motor size and a properly sized and bonded ground wire.
More about GFCI Circuit
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
For more information about Circuit Breaker
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
This link is helpful as a Contractor
Electrical Code Articles
|« How To Install A 3-Way Motion Sensor Switch||Wiring For Clothes Dryers – Don’t Do This »|
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.