Help for Bathroom Light Circuit Problems
By Dave Rongey - Summary:|
How to Troubleshoot and Repair a Bathroom Light Circuit Problem: Bathroom Light Power Source, Inspecting the Light Switch and Fixture and Checking the Wiring.
How to Fix a Bathroom Light and Outlet Problem
- Checked the Circuit Breakers
I looked at the breakers to see if any of them were tripped and they weren’t. I turned them all of anyway and turned them back on.
- Restored the Power
Everything came back on in the bedroom and bathroom but when I turned the lights back on in the bathroom it did the same thing.
- Lost Power
Now nothing will come on.
This electrical wiring question came from: Heather , a Homeowner from Knox, Indiana.
Thanks for your electrical wiring question Heather.
Application: Repair a Bathroom Light Circuit
Skill Level: Intermediate to Advanced
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester or Continuity Tester
Estimated Time: Depends on experience and level of problem solving skills.
Precaution: Testing live wires is dangerous and should be done by an experienced individual only. Testing using a continuity tester should only be made after the circuit has been identified and turned OFF and Tagged.
How to Troubleshoot and Repair a Bathroom Light Circuit Problem
- Bathroom Light Power Source
It is possible that the vanity light power source comes from a GFCI outlet that is located in one of the bathrooms.
- Inspect the Light Switch and Fixture
Make sure the light switch and fixture do not have am accumulation of steam or moisture which can cause the GFCI outlet to trip off.
- Check the Light Bulbs and the Fixture
Replace any light bulbs that may be faulty. Up to this point, if everything looks OK then the wiring of the light fixture and the circuit splice connections will need to be checked for a bad or deteriorated connection and then repairs must be performed as needed..
- Reset the GFI Outlet
After the checks and repairs have been made turn off the light switch and reset the GFI Outlet by pressing in the RESET Button.
- Further Electrical Wiring Inspections
If the preceding checks did not reveal any problems then the circuit that supplies power to the bathroom lights will need to be identified and tested for the cause of the fault. All the affected lights that are controlled by the light switch should be opened so the electrical wring may be inspected for burnt wiring and faulty connections.
- Replace the GFCI Outlet
If the problem seems to be associated with the GFCI Outlet then the GFCI outlet may be faulty and need to be replaced.
More about Wiring for a Bathroom Light Circuit
Electrical outlet wiring
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
For more information about Troubleshooting Electrical Wiring
Troubleshooting Electrical Wiring
Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« How To Fix Your 3-Way Switches||How to wire a range for 3-wire and 4-wire cords »|