Home » Electrical Wiring Directory » Electrical Wiring, Outlets » 4 Comments
|« Should You Tap 220 Electrical Wiring for a 120 Volt Circuit?||How To Wire Half Hot Receptacles »|
How To Troubleshoot Electrical Outlet Wiring Problems
By Dave Rongey - Summary:|
How to Identify Electrical Wiring Problems with Outlets: Checking Outlet Wiring, Troubleshooting an Outlet Circuit.
Wiring Problems with Outlets that Do Not Work
- There are five outlets on one circuit. The fourth outlet had power supplies for a cordless phone and charger plugged in.
- The phone was not working, and I noticed charring on the face of the outlet cover plate.
- The circuit breaker did not trip.
- I inserted a circuit tester and had the lights indicate the Hot and Ground are reversed.
- I have not worked on, or done anything with any of the electrical outlets on the circuit, however all outlets are dead, with the same indicator from the circuit tester.
- Should all of the outlets be checked for loose wires, wires touching, etc.?
Background: Robert, a Homeowner from Virginia Beach, Virginia.
Dave the Electrician’s Reply:
Thanks for your electrical question Robert.
How to Identify Electrical Wiring Problems with Outlets
- Application: Troubleshooting and Repairing Outlet Problems.
- Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrician.
- Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester or Volt Ohm Meter or plug-in circuit analyzer.
- Estimated Time: Depends on the age of the home and the condition of the electrical wiring and access to the circuit wiring to be inspected, evaluated and repaired.
- Precaution: Identify the outlet circuit at the electric panel, turn it OFF and then Tag it with a Note before performing any wiring inspections or electrical repairs. If an outlet or the electrical wiring is found to be damaged then repairs and replacement parts should be obtained with the same voltage and amperage rating.
- Checking Outlet Wiring for Electrical Problems
Yes Robert, every component of this circuit should be checked until the cause of the reversed reading is discovered.
- This outlet circuit should be identified at the electrical circuit breaker panel and turned off to prevent damage to other devices.
- Information that may help in the outlet electrical wiring troubleshooting process may be found in the listing below.
- Troubleshooting an Outlet Circuit
- Electrical troubleshooting for outlets is a process of elimination where components of the circuit are verified which helps to finally identify the problem and the make the necessary repairs.
- It is very helpful to remove or unplug any devices that are connected to the outlet circuit. Inspections for damaged wiring should begin at outlets that are used for devices that require high amounts of electricity such as space heaters, humidifiers etc.
Troubleshooting and Repairing Electrical Wiring
- Dave the Electrician explains the methods of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
For more information about Outlet Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
|« Should You Tap 220 Electrical Wiring for a 120 Volt Circuit?||Installing a Tankless Water Heater Circuit »|
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.