|« Electrical Wiring Diagrams and Symbols||How To Troubleshoot Wall Receptacle Problems »|
Installing a Occupancy Sensor Switch for a Bath Exhaust Fan
By Dave Rongey - Summary:|
Electrical Wiring Diagram for a Motion Detector Occupancy Switch for a Bath Exhaust Fan – The electrical wiring would be connected with the power source in and load out to the bathroom exhaust fan, a neutral wire if required and a ground wire.
How to Wire a Motion Occupancy Switch for a Bath Exhaust Fan
Background: Emmanuel, a Handyman.
Additional Comments: A very useful site. Keep up the good work!
Thanks for your electrical wiring question Emmanuel.
Wiring a Motion Occupancy Switch
Application: Wiring an Occupancy Switch.
Skill Level: Beginner to Intermediate.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with hand tools.
Precaution: Identify the light circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
Materials: Make sure the occupancy sensor has the same amperage and voltage rating for the electrical load, and is fully compatible with the electrical circuit and the device it will be controlling.
Installing a Occupancy Sensor Switch in a Bathroom
- The occupancy sensor or switch is typically installed in the switch box on the wall.
- The wiring is straight forward except that some of these occupancy sensor switches require a neutral wire for the 120 volt applications.
- The electrical wiring would be connected with the power source in and load out to the bathroom exhaust fan, a neutral wire if required and a ground wire.
- Below is one example of a occupancy motion sensor switch wiring diagram which should be helpful.
- Please read the complete installation instructions for your specific motion occupancy sensor switch for your bathroom exhaust fan.
Wiring Diagram for a Motion Detector Occupancy Switch
More about Wiring a Occupancy Switch
For more information about Bath Exhaust Fan
Bath Exhaust Fan
Bathroom Exhaust Fan
Answers to all of your questions about installing a bath exhaust fan and your bathroom exhaust fan replacement project.
|« Circuit Wiring for a Sub-Panel||Wiring a Switched Outlet Combo »|
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.