|« Identifying The Cause Of a Dimming Light Circuit||Why The Oven Makes The House Power Go Back On »|
Receptacles Not Getting Full Power
By Dave Rongey - Summary:|
How to Get Your Wall Outlets and Receptacles Working Again: When Wall Outlets and Receptacles do not work or Do Not Have Full Power and the Voltage is Not Normal – This is a typical indication that a splice or connection to the neutral has been lost. This process of inspection should be made on all the working outlets and affected outlets until the problem is discovered.
Why Do I Have 70 Volts on a 120 Volt Receptacle?
- The house is from the 1930′s and there wasn’t a grounding system.
- The contractors added a grounding system and installed GFCI outlets in the kitchen and bathrooms, but the rest of the receptacles in the house are still only two wire systems with no ground.
- What could cause the low voltage at the receptacles and why would the neutral side read hot?
Background: Paul, a Student from Bremerton, WA
Thanks for your electrical wiring question Paul.
How to Get Your Wall Outlets and Receptacles Working Again
Skill Level: Intermediate to Advanced.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Testers and Meters.
Estimated Time: Depends on personal level experience, ability to work with hand tools and electrical troubleshooting skills.
Precaution: Identify the circuit, turn it OFF and then Tag it with a Note before performing any wiring or inspections.
Important: Electrical troubleshooting is best performed by a qualified licensed electrical contractor.
When Wall Outlets and Receptacles do not work or Do Not Have Full Power and the Voltage is Not Normal
- This is a typical indication that a splice or connection to the neutral has been lost.
- The best way to troubleshoot this type of electrical problem is to locate the upstream outlet that is working and giving normal voltage readings. Turn off the power to this circuit and then remove this outlet and inspect the wiring connections.
- Pay close attention to the neutral connections that may be made to the outlet or check any neutral wire splices.
- In several instances such as this a bad connection is found where the neutral wire pushes into the back side of the outlet.
- This is especially a problem in rooms where high consuming electrical devices are used such as portable heaters because the load of these devices is placed on and through every splice or connection within the circuit.
- Most of the time it will be the neutral side of the circuit that is affected.
- This process of inspection should be made on all the working outlets and affected outlets until the problem is discovered.
- If the problem is due to the push-in type of connection then replace the outlet and make a new splice and pigtail out with one wire that will connect to the neutral side of the outlet.
- This will now prevent the load of the circuit from passing through the outlet, but place the load path through the splice instead.
- Be sure to make a good splice and use the correct size wire connector.
- Home Electrical System Problems
- If most of the home power does not seem to be correct then contact your electrical utility company or provider so they may check their side of the electrical service to your home.
- If the electrical utility company reports that the electrical service power is OK, and the condition persists then it is best to contact a licensed electrician who can perform electrical troubleshooting tests to identify the electrical system problem and make the necessary electrical repairs.
More about Electrical Troubleshooting:
Wiring Electrical Outlets for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Electrical Grounding Methods and Requirements
Listing of electrical codes for grounding with examples of electrical grounding codes for home electrical wiring.
Home Electrical Troubleshooting and Repairs
Troubleshooting Electrical Wiring Problems
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Types of Electrical Testers
Using Electrical Testers
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
|« Wiring Pendulum Lights For A Creative Application||How Do I Wire a Remote Control Ceiling Fan? »|
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.